CPVC Schedule 40 and Schedule 80 pipe shall be manufactured in accordance to the requirements of ASTM F for physical dimensions and tolerances. ASTM F/FM Standard Specification for Chlorinated. Poly(Vinyl Chloride) (CPVC) Plastic Pipe Schedules 40 and View on Information Provider. Designation: F /F M – 02An American National Standard Standard Speciﬁcation for Referenced Documents ASTM Standards: D Practice for.
|Country:||Turks & Caicos Islands|
|Published (Last):||22 January 2011|
|PDF File Size:||14.65 Mb|
|ePub File Size:||10.20 Mb|
|Price:||Free* [*Free Regsitration Required]|
However, tests on larger pipe have shown these stress values to be valid.
Link to Active This link will always route to the current Active version of the standard. These notes and footnotes wstm those in tables and figures shall not be considered as requirements of the specification. Due to inherent hazards associated with testing components and systems with compressed air or other compressed gases some manufacturers do not allow pneumatic testing of their products.
The purchaser shall have the right to perform any of the inspections and tests set forth in this specification where such inspections are deemed necessary to ensure that material conforms to prescribed requirements. The producer may use his own or any other suitable facilities for the performance of the inspection and test requirements specified herein, unless the ashm disapproves.
The central section is that portion of pipe which is at least one pipe diameter away from an end closure. The test shall be conducted in accordance with 8.
In case of no prior agreement, any sample selected by the testing laboratory shall be deemed adequate. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
Your comments are invited either for revision of this standard or for additional standards and should be addressed to ASTM International Headquarters. Experience of the industry indicates that CPVC plastic pipe meeting the requirements of this specification gives satisfactory service under normal conditions for a long period at these pressure ratings.
The sustained and burst pressure test requirements, and the pressure ratings in the appendix, are calculated from stress values obtained from tests made on pipe 2 in. The tolerances for out-of-roundness shall apply only to pipe prior to shipment.
Methods of marking are also given. We need your help to maintenance this website. NOTE 3—Pressurized compressed air or other compressed gases contain large amounts of stored energy which present serious saftey hazards should a system fail astk any reason. If the document is revised or amended, you will be notified by email.
ASTM Fpdf – Free Download PDF
Originally approved in This specification covers chlorinated poly vinyl chloride CPVC pipes made in Schedule 40 and 80 sizes and pressure-rated for water. Your comments will receive careful zstm at a meeting of the responsible technical committee, which you may attend. This standard does not purport to address all of the safety concerns, if any, associated with its use. A superscript epsilon e indicates an editorial change since the last revision or reapproval.
Your Alert Profile lists the documents that will be monitored. We have no amendments or corrections for this standard.
Workmanship, Finish, and Appearance 7. Thank you for interesting in our services.
Included are criteria for classifying CPVC plastic pipe materials and CPVC plastic pipe, a system of nomenclature for CPVC plastic pipe, and requirements and test methods for materials, workmanship, dimensions, sustained pressure, burst pressure, flattening, and extrusion quality. Historical Version s – view previous versions of standard. As the voice of the U. Combining values from the two systems may result in nonconformance with the specification.
An American National Standard Designation: Proceed to Checkout Continue Shopping. Users of this standard are expressly advised that determination of the validity of any such patent rights, and the risk of infringement of such rights, are entirely their own responsibility.
Please fill this form, we will try to respond as soon as possible. These notes and footnotes c441 those in tables and figures shall not be considered as requirements of the specification.
Included are criteria for classifying CPVC plastic pipe materials and CPVC plastic pipe, a system of nomenclature for CPVC plastic pipe, and requirements and test methods for materials, workmanship, dimensions, sustained pressure, burst pressure, flattening, and extrusion quality.
These dimensions conform to nominal IPS dimensions. Included here are the criteria for classifying CPVC plastic pipe materials and CPVC plastic pipes, a system astmm nomenclature for CPVC plastic pipes, and requirements and test methods for materials, workmanship, dimensions, sustained pressure, burst pressure, accelerated regression, flattening resistance, and extrusion quality.
This standard has been approved for use by agencies of the Department of Defense. Add to Alert PDF. Within the text, the SI units are shown in brackets.